This section illustrates the costs of replacing the heating and hot water systems in 60 social housing flats with Kensa ground source heat pumps. The scheme features an individual Kensa Shoebox Heat Pump in each flat, connected to a Shared Ground Loop Array of boreholes.
We have provided a ground source heat pump design with schematic drawings and ground source heat pump installation costs for both self-financed and funded split ownership shared ground loop array options versus an electric night storage heater (NSH) alternative.
Kensa has calculated example costs below to illustrate the upfront finance required for self-financed and funded split ownership Shared Ground Loop Arrays in a typical retrofit housing development featuring the Kensa Shoebox heat pump.
Also included are expected running costs and income generated via the Non-Domestic Renewable Heat Incentive (RHI) over a 20 year period (the duration of the Non Domestic RHI), compared to an electric night storage heater system. For a bespoke quote please click here.
Heat Pump System
|System architecture||Shared Ground Loop Arrays|
|Total heat pump capacity||191.56 kW|
|Equipment type||30 x 3kW Shoebox & 30 x 6kW Shoebox|
|Potable DHW temp||60°C|
|Integral immersion heaters||No (DNO friendly)|
|Ground array type||Boreholes|
|Total depth of boreholes||3,853 metres|
*Boreholes based on average ground conductivity. Average 18 sq/m per property – each borehole serves a minimum of 2 properties.
Total Project Costs, Savings & Returns vs Electric NSH
Kensa Ground Source Heat Pumps & Shared Borehole Ground Array
|Finance Option||Self-Financed||Funded Split Ownership||Self-Financed|
|Lifetime Expectancy: Appliance||Up to 20 years||Up to 20 years||Up to 10 years|
|Lifetime Expectancy: Infrastructure||Up to 100 years||Up to 100 years||-|
|Carbon Saved vs. NSH (over 20 years)*||5,381 TCO²||5,381 TCO²||-|
|Local NOx Emissions Saved**||19.6 kgNOx/y||19.6 kgNOx/y||19.6 kgNOx/y|
|Appliance, Infrastructure & Project Management Cost ^||£698,500||£323,101||£189,000|
|Running Cost Savings vs. NSH (over 20 years)***||£484,045||£484,045||-|
|Servicing Costs Per Property (over 20 years)****||£2,000||£2,000||£2,000|
|ECO Funding Contribution||£53,805||£53,805||Not eligible|
|RHI Income (over 20 years)*****||£931,134||-||Not eligible|
|Net cost (after 20 years)******||£286,439 profit||£269,296 cost||£189,000 cost|
*Carbon saving based on carbon emissions of 0.519kgCO2/kWh for electric. Assumes 100% efficiency for electric and 300% efficiency for ground source heat pumps. **NOx emission based on 44mg per kWh based on a worcester greenstar combi. ***Based on electric at 15p/kW/hr and COP of 3. ****Ground source heat pumps have no requirement for annual maintenance. However, it is good practice for the heating distribution system to be proactively checked and maintained to ensure optimum performance G3 Cylinder check will be requried. *****The Non-Domestic RHI is a 20 year index linked funding stream which assumes inflation at 3%. ******Net cost does not include servicing and running costs. ^ Retrofit costs include internal fit out i.e. new radiator systems. Tenant network connection fee applies.
Cumulative Deficit / Surplus Over 20 Year RHI Period
Counterfactual based on electric NSH costs Get A Quote
Ground Source Review: Chestnut Mews & Aspen Mews. As a result of the successful deployment of Kensa ground source heat pumps into 133 bungalows owned by Trent & Dove Housing, the housing association subsequently commissioned a second phase of installations for two blocks of three-storey flats. Winner: District Heating Project of the Year (H&V News Awards…
This Kensa Contracting commissioned animation depicts the key stages for the installation of Kensa Shoebox ground source heat pumps into individual flats in tower blocks, connected to shared ground loop array boreholes. For more information on this application click here.
Download Kensa’s two-page guide to funded Shared Ground Loop Arrays in new build developments, including funded project examples and details of the funding mechanism.